Invertor On-Grid trifazat Sungrow SG33CX-P2, 33 kW, 36300 W

Invertor On-Grid trifazat Sungrow SG33CX-P2, 33 kW, 36300 W la doar 12323.91 lei!

SG33CX-P2 este un invertor on-grid trifazat de la Sungrow utilizat pentru a transforma energia electrica produsa de panourile fotovoltaice in energie electrica utilizabila pentru a fi livrata in reteaua de curent electric si in locuinte. Acesta are o putere maxima de 33.000 W si poate functiona cu panouri ce pot genera o putere de maxim 46.000 Wp. Invertorul are o tensiune maxima de intrare de 1100 V si o tensiune de pornire de 200 V. Tensiunea de lucru MPP este intre 160 V si 1000 V, iar numarul de MPP-uri este de 3 independente. Numarul PV string este de 2 per MPPT, iar curentul de intrare este de maxim 90 A (30 A * 3). In ceea ce priveste tensiunea nominala, aceasta este de maxim 36.300 VA, iar curentul nominal de iesire este de maxim 47.8 A (la 230 V). Curentul de iesire maxim este de 55.2 A. Tensiunea nominala de lucru poate fi intre 312 si 480 V, in functie de configuratia utilizata. Invertorul functioneaza cu o frecventa de lucru intre 50 si 60 Hz, avand 3 faze si un tip de conector faze 3-N-PE. In ceea ce priveste protectia, invertorul are polaritate inversa (DC) si scurtcircuit (AC), si o protectie impotriva curentului de scurgere. Acesta are un comutator DC si o functie de recuperare PID. Monitorizarea se face pentru curentul string PV, grid si impamantare, iar interfata de comunicare este RS485 prin care poti conecta un senzor de putere smart meter (se achizitioneaza separat) utilizat in vederea gestionarii inteligente a energiei cu ajutorul caruia se pot realiza comenzi dinamice rapide si precise in ceea ce priveste alimentarea. Optiunea de WLAN sau Ethernet este optionala. Invertorul are o eficienta maxima de 98.5%, un grad de protectie IP66 si poate functiona in temperaturi cuprinse intre -30°C si +60°C. Conectorul DC utilizat este EVO2 (max 6 mm²), in timp ce conectorul AC este terminal OT (16~35 mm²).

Categorie: Invertoare fotovoltaice
Subcategorie: Invertoare fotovoltaice
Brand: Sungrow